Confer with that product’s installation sheet for directions. Twist and take away mounting bracket to insert battery. Product Description Lutron’s ceiling-mounted Occupancy Sensors are wireless, battery-powered, passive infrared (PIR) devices that mechanically management lights by way of RF communication with a dimming or switching device. These Sensors detect the heat from people transferring within an space to find out when the area is occupied. The Sensors then transmit the appropriate commands to the related dimming or switching device to show the lights on or off automatically, offering both comfort and distinctive energy savings. Sensor doesn't perform satisfactorily from this location, it could also be moved to 1.4 Ifanother location by pulling the Sensor straight down and repeating steps 1.Three and 1.4. 1.5 If the Sensor’s efficiency is passable, it must be permanently connected to the ceiling tile, as described in section G. Permanent Mounting. Momentary Strong Ceiling Mounting Use this process if the Sensor will be mounted on a strong, continuous ceiling floor reminiscent of drywall, plaster, concrete, or wood. Two 3M™ Command™ adhesive strips are provided for quickly mounting and testing the Sensor on clean, solid ceiling surfaces. These strips are designed for simple, damagefree elimination and are usually not reusable. These strips shouldn't be used for permanently mounting the Sensor (see section G. Everlasting Mounting ). Rigorously follow the elimination instructions under to make sure the ceiling will not be broken during removing. Observe: Don't use the adhesive strips on ceiling tiles, as they'll probably cause injury to the tile upon elimination. Simple-to-comply with Instructions Set-Up To ensure that the Sensor to operate properly, it should first be set up with a corresponding dimming or switching system. The process for organising a Sensor with a Maestro Wireless® (MRF2- solely) Dimmer or Electronic Switch is detailed under. P/N 041-172a 2.1 Peel the crimson "Command Strips" liner off of one of many adhesive strips and apply the strip to the flat facet of the mounting bracket as proven within the diagram. Notice: Do not cover the bracket’s screw holes because they will be used to mark screw gap areas on the ceiling. Organising a Sensor with a Maestro Wireless Dimmer or Digital Swap Dimmer Key Features · Low Maintenance. 10-12 months battery life. Convenient low-battery indicator. · Multiple Devices. Up to three Sensors can work together to regulate lights for broader protection in large areas. Every Sensor could also be added to as much as 10 receiving gadgets. Sensor Operation Occupancy Model - The Sensor will robotically turn the lights on when the house is occupied and routinely flip the lights off after the space is vacated. The Sensor will routinely turn the lights off after the house is vacated. There is a built-in 15-second vacancy grace period that begins when the lights are robotically turned off, throughout which the lights will robotically flip back on in response to movement. This grace period is offered as a safety and comfort feature within the occasion that the lights flip off whereas the room continues to be occupied, in order that the person does not must manually flip the lights again on. After 15 seconds, the grace interval expires and the lights have to be manually turned on. This Sensor is a part of a system and can't be used to control a load with no appropriate dimming or switching system. Consult with the instruction sheets of the receiving machine(s) for set up info. The Sensor could also be installed as much as 60 ft (18.Three m) away from the associated dimming or switching system(s) if they are in direct line of sight. If there are partitions or different barriers between the Sensor and receiving gadget(s), the Sensor must be positioned within 30 ft (9.1 m). Warning: This product should not be used to manage tools which might create hazardous conditions, such as entrapment, if operated unintentionally. Sensor in a location the place it has a broad view outdoors the supposed area. If that is unavoidable, the lens might be masked to block the view of undesired areas (consult with section I. Lens Masking). This guarantee is in lieu of all different express warranties, and the implied warranty of merchantability is restricted to at least one year from purchase. This guarantee doesn't cover the cost of installation, elimination or reinstallation, or damage ensuing from misuse, abuse, or injury from improper wiring or installation. This guarantee doesn't cover incidental or consequential damages. LUTRON’S Liability ON ANY Claim FOR DAMAGES ARISING OUT OF OR IN CONNECTION WITH THE MANUFACTURE, SALE, Set up, Supply, OR USE OF THE UNIT SHALL Never EXCEED THE PURCHASE Worth OF THE UNIT. This warranty provides you specific legal rights, and it's possible you'll produce other rights which range from state to state. Some states do not allow the exclusion or limitation of incidental or consequential damages, or limitation on how long an implied guarantee could last, so the above limitations may not apply to you. Patents pending. Lutron, Maestro Wireless, and the Sunburst brand are registered trademarks and Radio Powr Savr is a trademark of Lutron Electronics Co., Inc. ANSI is a registered trademark of the American Nationwide Standards Institute. IEC is a trademark of the International Electrotechnical Fee. Made and printed within the U.S.A. 25/09/09 P/N 041-172 Rev. A eight ft (2.4 m) 18 x 18 ft (5.5 x 5.5 m) 13 ft (4.Zero m) 9 ft (2.7 m) 20 x 20 ft (6.1 x 6.1 m) 14.5 ft (4.4 m) 10 ft (3.0 m) 22 x 22 ft (6.7 x 6.7 m) 16 ft (4.9 m) 12 ft (3.7 m) 26 x 26 ft (7.9 x 7.9 m) 19 ft (5.8 m) Momentary Mounting Methods 1.1 1.2 Insert the ceiling tile mounting wire by way of the two smaller holes in the mounting bracket and substitute the mounting bracket. Mount Sensor to a ceiling tile by inserting the wire legs by way of the tile, ensuring the Sensor is flush to the tile. Notice: Don't twist wire legs collectively. 1.2 After the Sensor has been briefly mounted, leave the Sensor in place on the tile and either take the tile down or remove an adjoining tile to gain entry to the legs of the mounting wire on the again of the tile. Low Exercise: That is probably the most sensitive setting and will detect very slight motions. That is the beneficial setting, as it'll work nicely for almost all applications. It is good for areas where occupants will often be seated for long intervals of time. Twist the wire legs together tightly so the mounting bracket remains snug against the tile. This setting is slightly much less sensitive than the Low Exercise setting and can be utilized for spaces that experience regular exercise. That is the least sensitive setting and can be utilized for spaces that will generally solely expertise large motions, equivalent to foot visitors. The Low Activity setting is the default and can carry out best for most functions. Hardly ever, if the Sensor is positioned close to external noise sources such as heating vents, air conditioning vents, or mild bulbs, it might flip the lights on without occupancy or keep the lights on too lengthy after vacancy. If this occurs, altering the sensitivity to Medium Activity or Excessive Activity ought to resolve the issue. Substitute the tile. Permanent Solid Ceiling Mounting 2.1 2.2 2.Three Superior Set-Up Operation The superior set-up is accessed by using the buttons on the again of the Sensor. Drill two 3/16 in (4.6 mm) pilot holes for the provided screw anchors. Press the anchors into the holes and faucet flush with a hammer. To show the current setting, press and release the desired button. An LED will illuminate briefly, indicating the current setting. Place the flat aspect of the mounting bracket in opposition to the ceiling and set up the two supplied screws utilizing a hand screwdriver. To adjust a setting, press and hold the specified button till the LED corresponding to the current setting begins flashing rapidly, indicating the setting can now be adjusted. Every subsequent button press of lower than 2 seconds will increment the mode to the next accessible setting. Urgent any of the opposite buttons will don't have any impact. To save lots of the selected setting, press and hold the button until the LED turns on stable, indicating the saved setting. During the adjustment procedure, if there is no activity for 30 seconds, the LEDs will turn off and no settings can be saved. Be aware: Don't over-tighten. 2.Four Attach the Sensor to the mounting bracket by inserting and twisting in a clockwise course till the Sensor locks into place. To remove the bracket from the ceiling, grasp the removing tab on the adhesive strip and pull the tab VERY SLOWLY straight across the ceiling, stretching the strip until the bracket releases from the ceiling. Discard the strip. By no means pull the strip at an angle, as it might break or harm the ceiling floor. Be aware: Don't pull at an angle. Lens Masking (Optional) Each time possible, the Sensor must be put in in a location where it can not simply see into areas outdoors the supposed area, similar to hallways or adjoining rooms. If this case can't be avoided, parts of the lens may be masked with the supplied labels to dam the Sensor’s view of the undesired areas. It is strongly recommended to remove the Sensor from the mounting bracket before applying Superior Set-Up (Elective) the masking labels. The Sensor features a number of advanced set-up modes. For the majority of installations, the default settings will provide the very best efficiency and you is not going to need to utilize the superior set-up. The Occupancy model of the Sensor has three adjustable superior set-up modes: Timeout, Auto-On, and Sensitivity. The Vacancy-Only model has solely two modes (Auto-On not obtainable). The default settings are listed under. The Sensor will be screwed onto the mounting bracket in several totally different orientations. Make certain to notice the Sensor’s orientation before taking it down and replace the Sensor in the same orientation to make sure the intended area will get blocked. Outer lens sections correspond to the detection regions furthest away from the Sensor, whereas internal sections correspond to areas nearer to the Sensor. Watch out when making use of the labels to avoid creating gaps between adjoining masked sections. The Sensor could detect motion through inadvertent gaps. Always (Occupancy version only) Timeout 30 min 15 min 5 min Auto-On All the time Low light Disable Activity Timeout 30 min 15 min 5 min Advanced Set-Up Modes Auto-On Always Low mild Disable Activity Activity: Low Activity Lens sections shown in white are masked with labels Timeout The Sensor will turn the lights off if no movement occurs for the duration of the timeout interval. There are three out there timeout settings: 5, 15, and half-hour. Lens Mask Lens sections proven in grey have not been masked Auto-On The automated-on performance of the Sensor can be adjusted to regulate how the lights reply upon initial occupancy. There are three available settings: At all times, Low mild, and Disable. All the time: The lights will all the time activate. Testing Sensor Coverage With the Sensor mounted on the ceiling, press and release the "Test: Sensor" button on the entrance of the machine. The lens will glow briefly, indicating the check mode has been entered. Note: There is a heat-up interval of roughly 40 seconds after the batteries are put in before the take a look at mode can be activated. If the button is pressed during this time, the lens will flash continuously until the heat-up interval is complete, and then the take a look at mode will probably be routinely entered. Confirm the coverage space by walking by the house and observing the lens. The lens will glow solid each time motion is detected. If the lens remains off during motion, the Sensor can not detect movement at that location. Press and launch the "Test: Sensor" button once more to exit the check mode. If the button shouldn't be pressed, the take a look at mode will routinely day out 15 minutes after being enabled, or 5 minutes after the final detected motion if the room is vacated. If the Sensor has significant hassle detecting movement throughout the test, it should be moved to another location and retested. If the Sensor still has poor detection from the new location, confer with the Troubleshooting section. Temporary Drop Ceiling Mounting Use this procedure if the Sensor will probably be mounted on a ceiling tile. The ceiling tile mounting wire is supplied for each non permanent and everlasting mounting of the Sensor to drop ceilings composed of a number of tiles. It's designed to permit temporary mounting, testing, and repositioning (if essential) of the Sensor with out damaging a ceiling tile. Once the Sensor’s closing position has been chosen, the mounting wire could be twisted to lock the Sensor in place completely. If the Sensor protection and wireless communication checks have been efficiently accomplished, use the mounting bracket as a template to mark the screw gap areas with a pencil. Word: Pull very slowly. Max. Room Dimensions Radius of Protection for Complete Coverage at Ground If you are uncertain about accurately positioning the Sensor, the next short-term mounting and testing procedures are really helpful to verify correct performance earlier than permanently putting in the Sensor. Sensor’s detection range relies on the ceiling peak, as proven within the desk beneath. Discover: Don't disassemble, crush, puncture, or incinerate the batteries. Don't dispose of batteries in regular family waste. Please recycle, take to a correct battery disposal facility, or contact your local waste disposal supplier concerning local restrictions on the disposal or recycling of batteries. O NOT mount the Sensor inside 4 ft (1.2 m) of HVAC vents or gentle bulbs put in beneath the ceiling line. Warmer rooms may reduce the Sensor’s capacity to detect occupants. Use solely excessive-high quality lithium batteries, size CR123, three V (ANSI-5018LC, IEC-CR17345). Do not use rechargeable batteries. Utilizing improperly rated batteries could injury the Sensor. For questions regarding the installation or operation of this product, name the Lutron Technical Support Center. Please present actual model quantity when calling. U.S.A. and Canada (24 hrs / 7 days) Setting the Occupancy Mild Stage (occupancy model, dimming devices only) the Sensor to the mounting bracket by inserting and twisting in a clockwise 2.5 Attach direction until the Sensor locks into place. Sensor protection and wireless communication tests as described in 2.6 Perform sections E. Testing Sensor Coverage and F. Testing Wireless Communication. The Sensor needs to be put in in a location where it has an excellent view of all elements of the room. The Sensor requires line of sight to operate correctly. If you can't see the Sensor, it cannot see you. The Sensor can't see through glass objects akin to patio or shower doorways. The range and efficiency of the RF system is highly dependent on a wide range of complicated factors such as: · Distance between system parts · Geometry of the constructing construction · Development of partitions separating system parts · Electrical gear located close to system parts Technical Assistance 2.2 Establish a location on the ceiling where the Sensor may have a good view of the room. 2.Three Remove the black "wall side" liner from the adhesive strip. The Sensor is designed for ceiling use only. Do not install on ceilings larger than 12 ft (3.7 m) or non-ceiling surfaces. Doing so may significantly inhibit the Sensor’s performance. 4. Do not paint Sensor. · · · · The "Lights On" and "Lights Off" buttons ought to now change the lights within the room on and off, respectively, when pressed. Repeat the above procedure to set up the Sensor with any further units. The Sensor is intended for indoor use solely. Operate between 32 °F and 104 °F (0 °C and 40 °C). 1.1 several seconds. Sensor that has been set up. After roughly 6 seconds, the lens will flash rapidly several times, indicating the sunshine degree has been saved. All Sensors arrange with the Dimmer will now use the saved occupancy mild stage. 2. Clear Sensor with a mushy damp cloth only. Do not use any chemical cleaners. Observe: This tools has been examined and located to adjust to the bounds for a category B digital machine, pursuant to half 15 of the FCC guidelines. These limits are designed to supply affordable protection in opposition to dangerous interference in a residential installation. This equipment generates, makes use of and might radiate radio frequency vitality and, if not installed and used in accordance with the instructions, might trigger harmful interference to radio and television reception, which could be determined by turning the gear off and on. The user is inspired to try to right the interference by a number of of the following measures: Reorient or relocate the receiving antenna. Improve the separation between the gear and receiver. Connect the gear into an outlet on a circuit totally different from that to which the receiver is related. Seek the advice of the dealer or an skilled radio/Tv technician for assist. Warning: Modifications or modifications not expressly approved by Lutron Electronics Co. might void the user’s authority to operate this equipment. This gadget complies with Half 15 of the FCC rules. This system should settle for any interference received, including interference that may trigger undesired operation. Swap 2.1 Set the Dimmer to the specified gentle level for entering the room. 2.2 Save holding the "Lights On" button on the front of a Word: For either Sensor model, the lights may also be manually turned off at any time by utilizing the dimming or switching system instantly. Vital Notes or Add the Sensor to the Dimmer or Switch by urgent and holding the "Lights Off" button on the front of the Sensor for approximately 6 seconds till the lens flashes briefly. The lights within the room may also flash three instances, indicating the Sensor has been efficiently added. The Dimmer or Swap will exit set-up mode robotically. The sensitivity of the Sensor may be adjusted based mostly on the anticipated degree of activity inside the room. There are three available exercise settings: Low Activity, Medium Exercise, and Excessive Exercise. Everlasting Drop Ceiling Mounting Note: Leave the removing tab uncovered previous the edge of the bracket so it may be accessed for removing later. 6 seconds until all LEDs on the system start flashing. Release the tap button. Sensor is detecting movement in areas that aren't fascinating, such as hallways or adjoining rooms, consult with part I. Lens Masking. If Sensor detection is satisfactory during this test, carry out the wireless communication check as described in part F. Testing Wireless Communication. Testing Wireless Communication This check needs to be performed to confirm that the Sensor has been appropriately arrange with the corresponding dimming or switching gadget and that there's proper wireless communication from the chosen Sensor location. If the lights within the room will not be on, flip them ON manually at the dimming or switching gadget. Press and release the "Lights Off" button on the entrance of the Sensor. The lights ought to turn OFF. Press and launch the "Lights On" button on the entrance of the Sensor. The lights ought to activate. If the lights do not reply correctly, check with the Troubleshooting section. Low light: The lights will solely activate routinely upon entry if there is not already sufficient ambient light in the room. Hallway falls within Sensor’s protection space. Disable: This setting converts the Sensor to vacancy mode. The lights is not going to routinely turn on however will still mechanically turn off after vacancy. The lights should be manually turned on by utilizing the related dimming or switching system. Note: The 15-second vacancy grace interval is energetic on this mode. Discuss with the Sensor Operation section originally of this document for extra details. Troubleshooting Symptom Possible Causes Solution Lights don't activate when area is occupied. Sensor shouldn't be appropriately added to dimming / switching gadget(s). Sensor’s Auto-On setting is about to "Low light" or "Disable". The lights have been recently turned off manually and the timeout has not but expired. Sensor does not have full view of room. Sensor is outside wireless vary of dimming/switching machine. Discuss with section B. Set-Up. Refer to part H. Superior Set-Up. Dimming/switching machine has been improperly wired. Light bulb(s) burned out. Breaker is off or tripped. Sensor’s timeout is simply too short for this software. Sensor does not have full view of room. Lens mask is improperly applied. Sensor’s sensitivity is just too low. Sensor’s timeout has not but expired. An exterior noise supply resembling an HVAC vent is interfering. Consult with section A. Pre-Installation. Behavior of lights doesn't match Sensor settings. Sensor coverage extends past room perimeter. The supposed setting was not saved. Multiple Sensors are added to a dimming/switching machine and their settings don't match. Seek advice from part A. Pre-Set up. Confer with part C. Sensor Placement or I. Lens Masking. Check with part H. Advanced Set-Up. Discuss with part H. Superior Set-Up. Sensor lens does not glow in response to movement throughout Sensor protection testing. Sensor cannot see motion attributable to obstruction. Room is just too large or oddly shaped. Move Sensor to another location. Seek advice from part C. Sensor Placement. A number of Sensors could also be crucial for full room protection. Try shifting Sensor to a new location or decreasing sensitivity. Confer with part C. Sensor Placement or H. Superior Set-Up. Lights turn OFF while area is occupied. Lights keep ON after house is vacated. Lens doesn't stop glowing during Sensor protection testing even when there isn't a movement. Lights don't respond accurately throughout wireless communication testing. Sensor lens flashes and lights do not turn on when area is occupied. Battery has been put in incorrectly. An external noise supply akin to an HVAC vent is interfering. Check with section C. Sensor Placement. Consult with part C. Sensor Placement or F. Testing Wireless Communication. Confer with part H. Superior Set-Up. Confer with section C. Sensor Placement. Seek advice from section I. Lens Masking. Refer to section H. Superior Set-Up. Check with part H. Advanced Set-Up. Attempt moving Sensor to a new location or decreasing sensitivity. Consult with part C. Sensor Placement or H. Superior Set-Up. Sensor will not be correctly added to dimming / switching machine. Sensor is exterior wireless range of dimming/switching gadget. Seek advice from part B. Set-Up. Transfer Sensor nearer to dimming/switching gadget and retry test. Discuss with part F. Testing Wireless Communication. Battery has been put in incorrectly. Dimming/switching system has been improperly wired. Light bulb(s) burned out. Breaker is off or tripped. Battery is low. Consult with section A. Pre-Installation. Remove sensor from take a look at mode. Confer with section E. Testing Sensor Coverage.
Feel free to surf to my web-site ... bbs.pku.edu.cn